I bought the Sonoff Touch for US version. I have installed and paired the device, now it is working with eWink. However, this device should never be sold to the US and will never pass the UL certificate. For the following reasons.
1. Basic design flaws. The US electrical wiring for home in wall installation basically takes the Romex or Beamex format and the wires they provided are solid wires(photo 1). The basic design for Touch dose not allow margins for the screws to protrude from the mounting braket. (photos 2 and 3). In order to install it, the bracket must be filed down with notches like the photos 2 and 3.
2. The latches of the Touch is too week to handle a solid wire installation(photo 4), basically it is about 1/2" from the wall bracket and the wires are exposed, After install the Touch, I have to use wires to tide it down (photo 5). This is absolutely not acceptable in electric code. In the US, plate covers are tide down with screws.
3. Apparently the switch require constant power to provide the wifi function. The US single cable (Romex or Beamex) wall installation comes in three wires, a ground, a neutral and a hot. The switch has provisions on neutral and hot wires, but has no provision for the ground wire. An ungrounded wire was used up to the 1960's but since 1970, it has been the standard for three wire grounded installation.
4. Most homes has three way switches. Touch has no provisions for a three way switches.
The whole Touch concept is fine, but you'd better come here to learn about electrical system and codes (law).
There is nothing in the US national electric code that prevents the use of stranded wire. It simply states it must be adequately protected where necessary. For instance, when ran in walls, it must be in a raceway or metal sheathing (FMC, etc). This isn't unique to stranded cable either, the same rules apply to solid wire ran in walls without an outer sheath (as in not romex).
When used in a receptacle box, the box provides protection, and there are no further requirements from the NEC, it is perfectly legal. In fact, you'd be very hard pressed to find solid conductors in many commercial applications, a majority use stranded THHN due to ease of pull through conduit and other factors.
One thing to watch out for though is make sure the terminations on the device are rated to accept stranded wire. If they aren't, that's a violation. For instance, a lot of receptacles and switches are only rated for solid wire. That doesn't really apply here though
Here is a discussion by industry electricians on the matter http://www.electriciantalk.com/f5/use-stranded-wire-20907/
NEC banning stranded wire is one of the oldest myths out there that just won't die
@Gary, but to have a US version that does not work in NA is not acceptable, it's false advertising because it does not work in NA. Actually it does but you have to have make lots of modifications to have it fit.
Thanks for the support. I have a non-metallic box, so I did get away with the screws protruding problem. But it is not upto the code to put flexible wires in a electric box, fire hazard. Also, extending the electric box by a surface mount will reduce your home value, it is not appealing. Maybe only in the garage.
My other problem still is the body of the touch cannot latch to the frame, so the tie down wire shown in one of my photo is still on.
After all, this is for the hobbyist, not a serious building material that can be sold in the US. I also think this will have problems world wide, just look at that Youtube video from New Zealand.
I give up.
I put stranded pig tails on since even the shorter screws would not sit flush when screwing down onto solid wire.
When I finally go to slide the switch into place, it stops short. Seems the body of the switch is slightly too wide to fit into a standard metal box! I can deal with shorts from the screws, put on insulation, cut out part of the box, whatever. How am I supposed to deal with a switch that is simply too wide (1.9") to fit into the box!! This is not some ancient non-standard box, it was installed when the home was built in 2005.
Glad I bought my first one from Amazon as a test, now I can return it with no hassle!
You should review this from Youtube
The screw you showed above is all the way in, if you have it half way, you cannot fit into the frame
Also, the two button Touch is not going to solve the three way switch. Please review the three way switch concept in the following youtube video
Please note that three way switch will not have full time power in each switch
I am sorry, Trevor, as far as I know, Itead has no intention to change its iTouch switch and it won't get UL or Canadian safety approval. Its product still remains in the "Hobbyist" category as far as I am concerned. Although one of the iTouch I have installed has been functioning for over one year. I always kept my old switch for future swap out if I were to sell my house, nevertheless.
I have also contacted support re: touch US version stating all the same concerns. I feel Sonoff must redesign and ship out replacements to every US user starting with all of us who have complained.
This is a workaround:
Mount the touch utilizing a surface mount box
you do not need to use the silver plate but you must buy some 1.5" box screws while at the store. Eliminate the rectangular plastic mount plate from Sonoff and either grind holes in the HD box to accommodate the latches or just cut them off. Remove the decor plate from touch and drill two box screw holes in the switch then you can mount the touch to the surface mount box and the too long screws they used will not be a short danger. I also use 14awg silicone jacket ultra flexible stranded wire pigtails on the touch, this makes it much easier to install b ut you are left with a unit that protrudes like any surface mount switch would. There really is NOT enough room in a one gang for this touch to safely reside. THEY REALLY NEED TO REWORK THEIR US DESIGN AND I HAVE DEMANDED THIS IN MY SUPPORT TICKET.
Sonoff dual maybe able to fix the three ways switch problem, but do we have to flash it with ESPurna to perform the operation or it has firmware included. Besides, it is the regular Sonoff, it has not been released to Touch and when it is implemented, will that fix all the problems that Touch has?
I still cannot make the touch to hold solid in the electrical box.